The purpose of valve acceptance? Through acceptanc...MORE >>
Under normal circumstances, industrial Check Valves are […]
Under normal circumstances, industrial Check Valves are not subjected to strength tests when in use, but after repairing the valve body and bonnet or the valve body and bonnet damaged by corrosion, the strength test should be conducted. For safety valves, the constant pressure and return pressure and other tests shall comply with the specifications and relevant regulations. The valve strength test and valve sealing test should be done on the valve hydraulic test bench before the valve is installed. Low-pressure valves should be spot-checked 20%, if they are unqualified, 100% should be checked; medium and high-pressure valves should be 100% checked. Commonly used media for valve pressure testing include water, oil, air, steam, nitrogen, etc. The pressure testing methods for various industrial valves including pneumatic valves are as follows:
1. Pressure test method of globe valve
In the strength test of the shut-off valve, the assembled valve is usually placed in a pressure test frame, the valve disc is opened, the medium is injected to the specified value, and the valve body and valve cover are checked for sweat and leakage. The strength test can also be carried out in a single piece. The tightness test is only for shut-off valves. During the test, the valve stem of the shut-off valve is in a vertical state, the valve flap is opened, and the medium is introduced from the bottom end of the valve flap to the specified value. Check the packing and gasket; close the valve flap after passing the test, and open the other end to check for leakage. If both the valve strength and tightness tests are to be done, the strength test can be done first, and then the pressure is reduced to the specified value of the tightness test, and the packing and gaskets are checked; then the valve flap is closed and the outlet end is opened to check whether the sealing surface is leaking.
2. Pressure test method of ball valve
The strength test of the pneumatic ball valve should be carried out with the ball half open.
Floating ball valve tightness test: put the valve in a half-open state, introduce the test medium at one end, and close the other end; rotate the ball several times, open the closed end when the valve is in the closed state, and check the sealing performance at the packing and gasket at the same time. There must be no leakage. Then introduce the test medium from the other end and repeat the above test.
Fixed ball valve tightness test: before the test, rotate the ball several times without load, the fixed ball valve is in the closed state, and the test medium is introduced from one end to the specified value; the pressure gauge is used to check the sealing performance of the inlet end, and the accuracy of the pressure gauge is 0 ．5~1 level, measuring range is 1.6 times of the test pressure. Within the specified time, if there is no depressurization phenomenon, it is qualified; then introduce the test medium from the other end, and repeat the above test. Then, the valve is in a half-open state, both ends are closed, the inner cavity is filled with medium, and the packing and gaskets are checked under the test pressure, and there should be no leakage.
The three-way ball valve should be tested for tightness at each position.
3. Pressure test method of butterfly valve
The strength test of the pneumatic butterfly valve is the same as that of the globe valve. The sealing performance test of the butterfly valve should introduce the test medium from the end of the medium flow, the butterfly plate should be opened, the other end should be closed, and the pressure should be injected to the specified value; after checking the packing and other seals for no leakage, close the butterfly plate, open the other end, and check the butterfly No leakage at the plate seal is qualified. The butterfly valve used to adjust the flow can not be tested for sealing performance.
4. Pressure test method of diaphragm valve
In the diaphragm valve strength test, the medium is introduced from either end, the valve flap is opened, and the other end is closed. After the test pressure rises to the specified value, it is qualified to see that the valve body and bonnet have no leakage. Then reduce the pressure to the tightness test pressure, close the valve flap, and open the other end for inspection. No leakage is considered qualified.
5. Pressure test method of check valve
Check valve test state: Lift check valve disc axis is in a position perpendicular to the horizontal; swing check valve channel axis and disc axis are in a position approximately parallel to the horizontal line.
During the strength test, the test medium is introduced from the inlet end to the specified value, and the other end is closed. It is qualified if there is no leakage in the valve body and bonnet.
In the sealing test, the test medium is introduced from the outlet end, and the sealing surface is checked at the inlet end. No leakage at the packing and gasket is qualified.